The BB2-7020-NB is most often used as a BACnet server, providing
LonWorks data to BACnet clients such as a building management
system. The BB2-7020-NB can also be confi gured as a
BACnet client, automatically reading and writing BACnet objects
in other BACnet devices to share LonWorks data.
The BB2-7020-NB provides a “pool” of 300 objects which may
be allocated by the user to the object types desired. Any mix of
Analog, Binary, and Multi-state Input, Output, and Value objects
may be allocated. Output objects are commandable and include
the standard priority array found in commandable BACnet objects.