The BB2-3020 is most often used as a BACnet client, but it can
operate as a server. This makes it possible to put LonWorks devices
on a BACnet network (but does still require binding and network
commissioning with LonMaker or equivalent).
The BB2-3020 provides a “pool” of 300 objects which may be allocated
by the user to the object types desired. Any mix of Analog,
Binary, and Multi-state Input, Output, and Value objects may be allocated.
Output objects are commandable and include the standard
priority array found in commandable BACnet objects.